Welcome!On this forum you can discuss iRidium with other users. iRidium consist of 2 main components - i3 pro app and iRidium Server. Please post here your questions, ideas or errors you find.
Please send your questions to support team as a private messages.
ALL the new HDL Wireless devices have also a 4channel drycontact input. When an input is changed, the modules automatically send out a "Dry contact broadcast message". But iRidium does not recognize these messages. So you have to repeatly request the status of each channel on every wireless device over and over again. Please include the broadcast message datagram into iRidium PRO as soon es possible, so iRidium can react directly to an input change. And also decreasing the bus traffic!
I attached a screen shot. I have a status request for channel1 and channel2 running every 10 seconds. When the status changes, you see that the module automatically send out a broadcast of each channel that is changed (Line 39 and 51). In this case channel2 changed from closed to open and back again to closed.
So, iRidium has to process the OP-Code 15D0 correctly!
Martin Lang - MEB Austria
Add the scan by subnet and id.
In BUS Pro software we have a "fast" scan. Shows not all devices in big installations.
And precise scanning by id.
Iridium have only fast scan with time limit.
And it find devices with id 6 then 2 then 9 or something.
Please add scan by device id please.
would it be possible to add a function in the upcoming i3-Gate to automatically update the Logic-Module (HDL-buspro) in a regular interval (once a day) to keep the Logic-Module which broadcasts the time/date to panels and internal logic functions up2date on "DaylightSaving"-Changes.
I checked out the communication protocol via UDP to the logic-module if you need that info.
So when using the i3-Gate with HDL-buspro this would be an awesome add-on. Its really annoying to allways login to the HDL logicmodule and do a time-change so that the client sees the correct time on the DLP panels.
With best regards,
Martin Lang - MEB Austria
please include the latest HDL wireless components correctly
into iRidium 3.x
for example there are new "1channel relais", "2channel relais", "1channel curtain control" out
with changed id-codes depending on a new firmware in these modules. iRidium doesn't recognize
also, all these new HDL wireless devices have 4-dry-contact inputs.these should be also included
directly into each device. otherwise we allways have to write additional devices and give them the same subnetid/deviceid, thats bad.
also the outdoor microwave/lux/humidity/temperature sensor is not recognized corrects, along with the wireless dlp panels! they have inbuild dimmer support.
and last big question, is it possible to clone/copy a self created hdl-device after setting it up with all the commands and feedback-channels needed? i can't see this option in the list?
I would like to use iRidium and HDL-Bus to control my lighting system by Lumencache. Lumencache control commands are vis RS232/485 (e.g., light fixture #1 ON command is [1,255] and OFF command is [1,0]). Has anyone used HDL-Bus Logic and universal switch for RS232 control? I'm having difficulty figuring out the programming with the online documentation.
Hello, I am using the yahoo weather program, when I use it, that program only works without problems, but when I enter it into another program, it does not work, does anyone help me?
Есть ли интеграция в ПО на уровне команд (не скриптов) MHRCU.433 версии Buspro? Интересует реализация проекта в 1 однокомнатной квартире с использованием i3 Pro или i3 Lite?
В проекте используются три 6-ти канальных модуля "HDL-MFH06_332 (6ch Floor Heating Module)"
С последним обновлением (1.1.7) стало невозможно получить от драйвера HDL в iRidium значения sampling temperature (Parameter=2) любого канала для всех модулей. При этом для фидбеков с "Read temperature New" все работает норм.
Для всех каналов "Ch Status OnStart" (Parameter=0) настроен таймер 60 сек.
some time the trigger butom work and some the time not in the same configuration i follow the instanractions and videos, can you connect remotely with me to help me in this issue
It seems that some of the channels are not synced with the actual status,
Some are on and not showing it and some are off and showing at i3 as On,
The feedback chanel is connected with each cjannel button of course.
What is the right way to get the channel status for each page\popup ?
Customer support service by UserEcho