Bogdan S 6 years ago in i2 Control V2.2 • updated by Aleksandr Romanov (CTO) 6 years ago • 1
From time to time the inteface stop working. I do not where is the issue but after I (warm, from KNX) restart the BAOS server Iridium also start working. The time gap between "frezzes" is not the same so there is no pattern. Ever heard of this problem with the v2.2?
Customer support service by UserEcho
We know that this problem sometimes happens in BAOS, it does not relate to iRidium.