Iridium And ETS Clima
Yeliz Tarhan 8 лет назад в Продукты / KNX • обновлен anonymous 8 лет назад • 2
We use air conditioning in the project.
We can not set point .The key is increased and you can see the project screen. It is not from the project. Value remains constant.
I am sending pictures of the ETS and iridium
Сервис поддержки клиентов работает на платформе UserEcho
Sorry for delay! It is possible that the ETS subtype has been set incorrect, start the ETS monitor and look at the data when you send the command from KNX push button and from iRidium, check the data type and make the same in iRidium and ETS
Also flags for datapoint in ETS need corection. For + and - buttons in iRidium it is needed that Read (R) fag to be set. In other case buttons won't know the real value and can't change it.
So you need to find real setpoint for your B.IQ and make sure that you can read and write it via ETS and only then import it in iRidium.